Another question on the same project as my others. While commissioning the system I observed that on full system power up sometimes the Flexy 201 would not write values to the PLC.
I am using the Flexy 201 to read modbus values and directly write them into a Allen Bradley PLC. To fix the issue while I was in the field I manually changed the value of the PLC from eWON web page and then it started writing as normal.
Just fishing but has anyone seen this or know why it may happen? I am concerned that this will happen again and cause a bigger issue.