I am using an Anybus gateway to communicate from a siemens PLC to a Allen Bradley PLC. I am working on checking data mapping points and have ran into an issue. We are sending and analog value from one PLC to another and we are not getting the correct values back. We notice that since we are sending integers it gets broken up into two bytes - a high and low. Noticing this we did a calculation to try and solve this issue but have no luck. Here is an example of our calculation - (DIG_DATA:I.Data * 256 + DIG_DATA:I.Data)/10. Do you have another solution?